Can a 3 port mid position valve be made to act as a divertor valve or do i need to buy a specific item? Looking round on the net, a Honeywell V4044C1288 seems to be the only 3 port 2 position valve around, everything else is the newer mid position variety. Ive noticed some have 3 wire and some have 5, does this have any bearing on the matter and can one be wired to do the full switch and not stop midway? :?
[size=9]I wont go into great detail cos its complicated and you'll all think I'm mad but....
Im trying to source a 3 port, valve that does just A or B acting as a divertor so that i can switch between a hot water cylinder running a 3 bar booster and an instant hot fed from my combi outlet. (Its a combi, but Ive retained the hot water cylinder using a Danfoss control pack). [/size]
Well, basically, both the three wire and five wire versions of the valve will do what you want. The extra wires in the five wire version just allow the valve to be held in the central position. The three wire version is used in a "W" plan and is designed to operate either A or B ports, but not both.
Google for Y Plan wiring or W plan wiring. Select the Honeywell website.
Also, check the topic further down this forum "Nightmare system wont turn off" has information about valve wiring.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!