I have installed a second light which I wish to run off the existing switch. The existing pendant has 3 lots of 1.0mm t&e running into it. Do I connect via jb to one of these or do I connevt straight into pendant with my 1.0mm t&e from my new light? Thanks
Years ago the ceiling rose was always used as a junction box to next light which was handy for emergency lights and ceiling fans. However there was often no neutral at the switch.
Use of 12 volt lights with power supplies has changed this and some houses now use the switch back box as a junction box as there are no ceiling roses. This however increases the loop impedance and one does have to be careful volt drop is not exceeded.
Without knowing the system used can't really give an answer. However in the main to add a light you go from an existing to new lamp and then from new lamp to switch there is not normally any connection between switches unless designed to use transformers and the like.
Years ago some two way lighting did borrow line but it caused radio interference and the practice was discontinued.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!