They go with the rest of the sockets I have, planned to punch it into the wall above the en-suite door and wire upwards into the loft.
However, I stopped short on ordering with the lack of "double pole" in the description. Any recommendations or alternative methods or is my plan sounding ok? I don't really go much on the pull cords in the ceiling, feels like old peoples home decor :-)
At first glance it looks like you want to run an electric shower from the lighting circuit. You actually want to run a pump from a lighting circuit. Technically you can run a shower pump from a lighting circuit, but I would not recommend it. When a pump starts it draws a lot of current, this current may be enough to trip the lighting MCB. Also at night when the lights are on 3A (for the pump) may be "just too much" for the lighting MCB again causing it to trip. Lighting is often protected by a 6A MCB
I would connect your pump to the ring main if you want less / no grief.
[quote="kbrownie"]Not good practise supplying shower pump from lighting circuit, but I cannot see any danger with it, Providing the load/demand on the lighting allows this, without causing overloads and trips. But it would be recommended that the manufacturers instruction are also looked at.
What must be done, is that all newly installed equipment and circuits entering the bathroom, are RCD protected.[/quote]
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!