My bathroom light finally gave up the ghost the other day after the slow blow fuse melted into place. I haven't got the money to get an electrician in at the moment as they would probably take one look at the wiring in the house along with the ancient fusebox and end up billing me to do the whole gaff as it's 'not to current standard'. So nipped to B&Q and bought a cheap light thinking it couldn't be too hard to wire in.
I have two red wires, two black wires and two green and yellow wires coming from the ceiling. Now I know that the old red wires were the live, the black were the neutral and the yellow/green is the earth. All seemed simple enough, wired it in as per the leaflet enclosed (live to live, neutral to neutral with the earth insulated and isolated. Only trouble is the light stays on all the time.
Now, the leaflet enclosed with the light mentioned "live loop wires" and stated there were normally two of these and they should be insulated and isolated inside an addtional wire casing which was enclosed. Only having two of each wire I guessed that maybe mine only had one "live loop wire". So I alternated each wire into the additional casing with the other one wired in and vice versa - still no joy. Light stays on and the wife sitting on the sofa taking the mick out of my DIY skills (or obvious lack of them should I say).
Not being lucky enough to know anyone who is a sparky or with the remotest idea about wiring I am stuck with a dark bathroom when the sun goes down. Am sure there is a simple solution and I was hoping that someone in here might be able to lend a helping hand with some friendly advice.
Thanks in advance,
Your two reds should be connected together (in casing provided) and not terminated to the light. One is Live and the other is switch wire.
The two blacks one is neutral and should be connected to the neutral terminal on light at blue side of lamp flex and the other is return from swicth which will offer a live to light when switch is closed and should be tagged with brown (used to be red) sleeving and terminated at the live, brown side of lamp flex. all earths together and that should do the trick!
Remember to be safe and isolate circuit before any work is carried out and ifyour house wiring is sub-standard i'd consider a re-wire but get a sparky to look at it.
Did this light work before you decided to change it? because that is the standard format for end of loop connection. Is the swicth wired correctly? and has any other worked been done that could have effected this circuit?
Did you understand my explanation? look at projects on this websites under electrical lighting it may show some diagrams that are helpful!
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!