I had an electrician around at the weekend to fit a new consumer unit and bring our bathroom within Part-P regulations. As we have a shower cubicle and the light is in Zone 2 we have to have a sealed unit which he supplied and looked like it should be in a public lavatory. I sourced another from Screwfix which has an 11watt energy saver bulb but barely lights the room. Does anyone know of any stylish lights to meet the criteria which would possibly produce more light?
It is unusually to have ceiling below 2.25 meters high (Zone 2) but where they are than IPXXB or IP2X for plus IPX4 or if exposed to water jets, e.g. for cleaning purposes, IPX5 is limiting factor as well of course as having an RCD.
XXB = Protected against access with a finger (minimum 12 mm diameter test finger, 80 mm long) (adequate clearance from live parts).
2X = (a) Protection against access to hazardous parts with a finger
(b) Protection against solid foreign objects of 12.5 mm diameter and greater.
IPX4 = Protected against water splashing from any direction
IPX5 = Protected against water jets from any direction
So either IP24 or IP25 in real terms you can forget about the IP2X as if to IPX4/5 it will be better than IP2X.
There are loads of lamps that comply with this just go to local whole sale outlet.
There is no such thing as a Part P consumer unit. There are consumer units which can easy be configured to BS7671:2008 which will normally have at least two RCD's and bathroom lights will now be covered by an RCD.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!