I would be grateful for some advice on a wiring issue i have. I have fitted a new ceiling fan\light in a front room the unit has two pull cords one for the fan and one for the light, these function correctly ie switch it on\off and fan speeds. There are two single switches at either end of the room but none of them are working now with the wiring connected as shown. What confuses me is with the old fan light unit nothing was connected to the block marked ? but the switches worked ok. Your help is much appreciated.
Looking at your wiring diagram, it looks like you have connected the fan/light directly to the permanent live, instead of the switch line. That is why the pull cords will operate both light and fan and the wall switches will not.
The brown cable of fan/light that is terminated to the loop with the three reds in, wants to be removed and terminated with the single red at the question marked block.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!