I have balanced some of the Rads today and found 1 rad was cool so i bled the system but unfortunately the bleed nipple in the rad came out - water squirted everyehwre .
Anyway bleed nipple back in OK and now the heating system refuses to start up - the boiler kicks in but then the overheat thermostat trips .
When system is left for 1/2 hour or so then boiler works for a while then clicks off again.
Water pump works but gets very hot with pipes eirther side of pump at lower temp - any ideas greatly appreciated .
Has to happen on the coldest night so far !!!!
I checked the pump and it WAS stuck so I shut off either side removed the pump to check it and it was dry inside which bothered me - I then tentatitively checked the feed and no water which means the rad issue I had vented out all the water and i was left with an airlock - I cleaned the feed pipe out and loads of sludge came out but I then got water so had my feed back.
Put pump back in - circulated the system and now I have full heat again .
Thanks again for your help
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!