Im completely clueless at electrics. I have purchased 3 new ceiling lights. 2 i have wired up no problems. However when i fooloishly tried the third, i noticed that there were many more wires than the other 2. I mixed the wires up and now cannot reconnect them. All 3 lights now do not work (the other 2 did until i tried wiing the third).
All the three lights are down stairs (kitchen linked dining room linked extension).
The kitchen light and the dining room light run off a 2 way switch, the extension runs off another switch (which links to 2 more lights on a 3 ay switch).
I hope that makes sense to those in the know?!? Im currently typing this in the dark as ive managed to blow the fuse for all the downstairs lights...................................HEEEEELLLLLLLLLPPPPPPPPPP!!!!
PS the house is not new build if that makes a difference?
Hi, tried to follow but lost plot near the end!
Please, what colours do you have at your light, how many of each colours, how should it be switched, can you find the wire from the switch?
If all cables are Red/Blks (+earths) & if 3 sets, then three reds go together in spare term. block,(not connected to fitting).
one Blk. comes from switch & should be marked as sw. line with tape/sleeving (red), it goes to live connection in light (to brn flex).
Two remaining Blks are neutrals which both go to fittings Neutral
Earths go to earth term in fitting.
hope this helps,regards SPARX
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!