Im in the process of trying to replace a light fitting (lamp with 5 bulbs) that is controlled by a dimmer. Unfortunately, as the ceiling was replastered, the light fitting was taken off and I am having difficulty trying to work out the wiring as the colour scheme does not match....
Out of the ceiling I have the following wires, two black, two red and one green. My first attempt at doing this made the light stay on permanently and after this I gave up.
Does anyone know how the wires are meant to be configured?
I would guess two reds into loop (This does not connect to light it's self) then black with red sleeve to brown (Line) and black without sleeve to blue (neutral) and earths to metal. If two blacks are wrong way around it still should work.
hi under 'projects' @ top of screen is a list of items freq. occuring, this being by far the most common!
If you find one on changing a light fitting it's all there in colour.
basically if you only have 2 twin/earth cables then simply put the 2 reds in a spare connector together (not connected to light) one black to each flex term (blue & brown) plus earths to earth term on light.
You say one green but it will be 2 single earth wires sharing green sleeving, one from each cable.
If you have tried it with 2 reds together & 2 blacks together you may have 'Fubar'ed' the dimmer!
Always work with circuit dead!
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!