I have purchased a ceiling light from Italy which has come with no instructions. It has two wires, both clear in colour which I have connected to the existing live and neutral which caused it to blow the fuse. I then did the above and also connected the earth which had the same result. Thanks for any advice.
You will have live, neutral, earths and switch cables in the ceiling void.
You need to connect earth to earth terminals,
all the reds together in a seperate termination block with nothing else and you should then be left with two black may be three blacks if you also had three reds.
One black is a swith live and the other(s) neutrals. The switch wire should have a red tag on it but this seems to be often forgot about.
The switch wire will go to one side of your lamp(clear cables) and the neutrals to the other.
This should now work. Isolate circuit prior to work
I am assuming your cable colours are the old red and black, but the new colours in recent builds are Brown instead of Red and Blue instead of Black.
Did you also alter the existing ceing rose connections?
How many wires have you in the ceiling rose /connector and what colours are they?(exclude earths)
What type of lampholder does the fitting have(BC,ES,SES)?
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!