Can someone give me a solution to this problem. The two water tanks in the attic I believe are hot and cold tanks. the samller for the heating(?) is always at a maximum level and every time the heating comes on always goes high and the overflow pipe starts to take away the excess water. the ballcock is old as is the connecter. I don't think the ballcock is working properly. Any ideas? Or do I have to replace the ballcock and connecter?
:cry: i,m afraid batty you may have a split coil inside your cylinder,i would seek a professional to explain,you may need a new cylinder.Its backing up the cold feed to your F&E tank.nothing to do with your ballvalve.Good Luck
You need to go into your attic ,get somebody to switch on heating and watch what happens,you could then where the tank is filling from . if the water rises in the tank on its own without any other influence,then it could be the cylinder.If water is pumping over from the expansion Iwould agree with my colleague.Both cases require a pro to prevent your system getting worse
My brother is a plumber and I've taken advice from him. I've installed a new ballcock but with my limited knowledge, whoever botched the job up years ago made a right hash of it. the tank is on a slant and the pipework looks second rate. Anyhoo, I know one cure for all of this and that's get a pro in and have a combi boiler fitted.
Thanks for all that have provided advice. The water in the tank is cold by the way. I've now got to resolve the airlock in the hot water
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!