hello people new to this forum :)
i have a problem in my bathroom, i bought a new flush light fitting and took down the old light hanging thingy, when i have stripped the light down to just the wires i stupidly took the loop off and have no idea how to get the light back working (so many wires)
i have 4 reds, 3 neutrals black,2 earth wire and 1 yellow and 1 blue i have no idea which one is the switched live or even if its a two way switch live as the lights in my hall and back bedroom do not work now
if anyone could help me i would much appreciate as i have no idea on how i put the wires together in the toffee block or loop :x
if you seperate all the cables (switch off supply before} with a mains tester and now with the mains back on test between all the reds to an earth cable,one of the reds will be live,you then need to identify the switch wire from the looped feeds,this can be done with a continuity test,connect the looped feeds together,the neutrals together and earths together,your new light can now be connected to the earth,switchwire and neutral, ( would strongly advise you to get an electrician to do this for you it can be very dangerous if you make a mistake, best of luck.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!