My house has an existing soil stack against a single storey part of the building that I want to put an additional point of entry higher up. The current entry point is just above ground level and the soil stack extends about 0.7m above the eaves. I want to connect an additional point of entry from another part of the building just below the eaves giving only about 1.1m of stack above this new entry point. Is this OK? :?: - Thanks - Mike
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!