I wish to install a light switch which has a small red warning light on it to replace my current standard switch. The current switch has 3 connections, brown is in L1, blue is in L2 and L3 is unoccupied. My replacement switch has four connections labelled L in, N in, L out, N out. how should I wire it?
The new switch is a double pole one gang with neon indicator. Your existing switch is 1 gang 2 way.
Your new switch ideally needs a neutral to work. Your existing switch has no neutral. (It has no need for one) The cables you have are live and switched live.
You can connect your new switch in place of your old one, and you maybe lucky in that the neon will illuminate (slightly) but that depends on what lamp you will be switching. It would have worked on an old incandescent lamp or even a halogen lamp, but if you have a modern LED chances are it will not illuminate, and even if it does, it will work in reverse. (When the lamp is on, the neon will be off, and when the lamp is off the neon will be on)
Also double pole switches often require a deeper than normal back box.
Thanks again Mr W. However, I still do not know which connectors to use. |f I am connecting to a live switched then am I correct in assuming that i should use "Live In" and "Live Out" simply ignoring the Neutral connectors?
I do have MiHome Energenie wifi light switches in my house that do not require a neutral and a red LED shows when on, but at over £16 it seems rather expensive for what you want, I use them in bedrooms together with remote control to turn off/on from in the bed.
However as Mr White points out they are deep, and I have spacers behind the switch to be able to fit it.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!