Hi, I’m normally an install engineer but today I’ve tried to run a newly installed mitsi split system but having the following issues. I’m trying to run it in cooling but it’s not really doing owt. Suction pressure drops to around 3 bar & suction valve frosts up, pressure then goes up to about 5 bar & condenser fan then cuts out for a few minutes. The frost evaporates off the suction valve & then the same process starts again. Put it into heating, indoor unit more or less shuts down just a slow fan speed. Outdoor unit kicks in after a few minutes then ramps right up but the suction pressure was 55bar and the valve was too hot to touch. The indoor unit just stays in low fan speed & no heat gets released. What could cause this? Sorry for being long winded
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!