I removed a downstairs radiator for plastering and painting but when i replaced it i lost about 3 litres of water because I opened the TRV accidentally :(
Now none of the radiators heat up. I tried bleeding them but only water comes out. The pump in the airing cupboard still sounds like it's working and I can hear water in it but it doesn't sound like it did. It's a Grundfos ups15-50 x6 model u747 and the copper pipes either side of it are warm but not hot . I have an old back boiler but unfortunately I dont know anything about it. My hot water is heated by an emersion so is unaffected.
I was hoping may be i pulled some air into the system when i had the little accident because it was working fine while the rad was off the wall but maybe I'm clutching at straws?
The system is airlocked - possibly at the pump, although if you only lost that small amount of water other things could be going on.
Whatever, simple bleeding the rads won't shift the fault. There is a big screw on the end of the pump. Remove it totally. Does it let air out? If no water weeps out, the system may not be filling properly - a header tank fault.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!