Long story... but.. in essence builder chappies have taken off ALL the downstairs radiators ( we have been flooded and the downstairs ruined ). However, we thought it prudent to put the rads back on in order to keep the ground floor warm during cold snaps etc. I have done this and bled them ( they are full of water ). The problem is that they will not run hot/warm when then upstairs rads are fine. Upstairs is 15mm piping and downstairs is 10mm microbore. If I open a drain tap attached to one of the downstairs rads... it will pour out hot water after a second or two. Once I close this off the rad, in question, will be warm/hot for 10 minutes then go cold again. WHAT IS GOING ON? WHAT AM I MISSING ?
Sitting in a caravan... in the rain... cold,fed up, wet with house like a bomb site!!
Close valves on all but one rad upstairs.
Open valves both ends of each rad downstairs.
Turn on heating.
If the downstairs rads don't run hot.
Check 22mm pipes out and back to boiler.
Is hot water getting round system?
Have you rebalanced system diverting all hot water upstairs while downstairs was unused?
Is hot water merely taking the easy route through the 15mm pipes?
Is the system zoned?
Has a motorized valve stuck/died?
Shut off all the upstairs rads., both valves, then do the same downstairs, except for one. Open its valves fully and bleed it. It should give flow and heat,top and bottom. Open another downstairs one, and almost ctose the simple isolator valve on your first success, retaining some flow. Establish flow one by one downstairs, throttling-down flow as you go. this is known as balancing rads.
When you return upstairs, the 15 mm bore will require less opening turns of the isolator valves, and of course the thermostatic rad. valves will only need settings of 4 or thereabouts.
Rads. that stay cool along the bottom, indicate sludge, which could well be a problem enhanced by microbore, but can be flushed, or powerflushed (costs Â£600).
Air-locking could still exist despite the above work, and could be shifted by a plumber.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!