Im replacing a normal light pull with a luxomat automatic pir light detector in my bathroom.
The exsisitng wiring has the normal connections id expect and the switch ghas a fan on a timer wired in also.
The new luxomat auto switch has a fitting ive never seen before, a push in connector for wires instead of conventional screw securing. Ive put test wire in but cant remove it, there are plastci clipe that seem to push in at top, but dont really do anything, ayn ideas!
Also the fiting is marked with one L and an arrow down terminal, two N terminlas and one L arrow up terminal, can anyone tell me what goes where please?
all else fails read the leaflet! this is far from straight forward as the switch needs a neutral to work its electronics, the connections being L in, sw. L out and N(s) of which you only need one. however I am sure I don't have to say again this is not DIY work, bathroom electrics are 'Part-p'
controlled service see doc's project section, it will need rewiring with a 3core & earth in place of existing twin/E
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!