Hi, I am looking to change from a normal light fitting to a fluorescent fitting in my garage. The light operates from two switches, one at the front and one at the rear of the garage. I have attached photo's of the existing wiring and also the connection points in the tube fitting. Can someone please advise me which wires coming in to the ceiling connection block go where in the tube fitting. The three connection blocks in the tube are labeled N, E and L (top to bottom). Is it as simple as getting the red incoming wires connected to "L", the black wire to "N" and connecting the yellow and green wire to "E" ?
I am also going to put a fluorescent in the loft. I currently have an inspection lamp at the end of a three core wire and plug it in to a switched socket on the landing when I go into the loft. Is it as simple as just removing the inspection lamp and wiring the fluorescent, brown to "L", blue to "N" and green/yellow to "E" Apologies if this is rock-bottom basic advice I am asking for but with electrics, some poor souls only ever make one mistake and I prefer not to.
On you existing ceiling rose, you have 4 connection points: *A switch line, that is where the single sleeved brown is terminated, this likely a a different colour core under the sleeve, possibly grey? *A live loop, that is where the two single brown cores are terminated *A neutral loop, that is where the single black core is terminate, this should really be sleeved blue! *A earth terminal, this where the green/yellow sleeved cables are terminated
So at the new fitting you have: * "L" which is where the switch line goes, single brown sleeved cable * "N" which is where the neutral loop goes, single black core * "E" which is where the earths go * There is no live loop on the fitting, so are going to have manufacture this yourself. A spare 5A connector block/terminal is required, where the two remaining brown cores can be terminated together, to form the loop, this is then left safely within the light fitting cover.
With regards to loft lighting, really not a good idea having a plugged in fitting on the landing. ideally a hardwired set up in the loft would be much better. But, yes if using a plug and flex, it is a simple as having, brown to live, blue to neutral and green/yellow to earth and having a 3A fuse in the plug. I would also clip/secure the flex in the loft space to rafters/joist to prevent it accidentally being pulled loose and becoming an electrical danger.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!