hi, most will need plastic small consumer unit eg 'garage unit' with tails connected to rcd main switch. Earth rod with earth connected to rod in pit or surface box, & to earth bar in 'garage unit'.
One local socket ,normally a double, connected to mcb, with test sheets filled in as far as possible ie all dead tests such as I.R. r1+r2 ect.
Fully marked and labelled with leckies name as responsible person, RCD & periodic test labels 'warning 230 V' labels inside and outside box.
Luck and a following wind helps too!!
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!