can anybody tell me the procedure for continuity testing the earth bonding of my copper pipework?
just done some plumbing work in the bathroom - i know for a fact that the pipes are cross bonded throughout the house as i've recently fitted a new combi and put in all new central heating, pipes and all, throughout and fitted the clamps myself. the clamps are only at the boiler, however. as all services, dhw, radiator f&r, gas and cold main all meet at the boiler is this the only place to cross bond?
i used an existing earth lead, (6mm earth cable) from the original system that i took out, to take it to earth. how do i test if this is sound and that it does actually go to earth somewhere?
i have a multimeter, just don't know quite how to use it for this particular type of test.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!