I need to fit a new spur to power a towel heater in my bathroom, but I am unsure of the location to place the spur!
am I right in thinking that the spur must be in zone 3 (min 600mm away from direct water ie bath or shower)
and is it ok for the towel rail to be partly in zone 2 (so long as it is IP4 rated!)
any help out there :?
Towel rails are one of the permitted items that can be used in Zone 1 and can be mounted above the bath but not in the bath not that it would really dry towels in that area! There is no Zone 3 in a bath room only 0, 1 and 2 and zone 2 only extends 0.6 meters horizontal from edge of bath.
The connection unit has to be suitable for the location and outside Zone 2 but can be within the 3 meters which is the closest that sockets can be mounted. I know it seems strange to put sockets in a bathroom but now there is no special regulation for showers in bedrooms and the 3 meter rule is really to allow sockets to be fitted in a bedroom with a shower is same room.
Do remember now all items in a bathroom need RCD protection.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!