The boiler as the following problem hope an expert can help me.
I turn the room thermostat to click (23degrees) & the boiler fires up. The temp dial on the boiler hovers around 60degrees for aprox 10Mins, flicking between hi/low flame. The flame then stays on high all the way from 60-88 degrees then the boiler switches back to a low flame & the boiler temp indicator keeps falling all the way back down to 60ish. During this falling temp period the flame doesn't go high again not even once. Only when i move the room thermostat to a higher temp it kicks back to hi flame but this time the boiler temp indicator rises to 100+ degrees â€“ I then manually switch the boiler off to be safe.
I managed to get an identical boiler off ebay to use as a spare & have since swapped the NTC resistor but still overheating.
I've been told that it could be the room thermostat (must admit it's quite old) or the swapped ntc could also be faulty (i think small chance having exactly same ntc fault).
Anyone any ideas? I know it's a long read but am desperate to get this sorted so have put as much info in as possible.
i would never recommend using a second hand boiler for anything - infact corgi will only allow it if it has been checked over - and certainly using second hand parts is not allowed
i am pretty sure that your model of boiler is about 20 years old which means it could have reached the end of its useful life(and done pretty well)
have you ever had to manually reset the overheat stat on the boiler?
do your radiators heat up?
the boiler does have an anti-cycle function which stops it relighting after a certain period of it reaching temperature, vaillants are also normally dependant on a lot of hydraulic compenents that can easily choke on older systems
if your radiators are not heating if may be the diverter valve sticking
Hi Guys thanks for the replies.
The boiler works fine with HW & CW only issue is occasionally it trips & requires a manual reset. I've noticed it trips out more often when its a very cold morning/night.
My room stat (newly fitted) is right next to the front door/hall way & the hallway is much colder than the rest of the house. This makes me think it could possibly be the location of the stat & not a boiler prob but i'm not 100% sure how the boiler should handle a situation where the stat is constantly calling for more heat. Should it cool down then start up again or should it keep heating to try & reach the stat temp?
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!