Hi all, hope some one can help me.
I have recently heard the water "hammer" in my house get worse, even at night!!!
This should not happen as heating is programmed to be off then.
I checked rads and they were hot even though controller was off!!
I switched controller from auto to off and same thing is happenng, some how heating is on with controller off !!!!
Ah ok, appologies, maybe hammer was the wrong expression, it is more of a creaking noise due to the heat expanding the pipes not the regular banging caused by high pressure water going round bends of loose pipes :lol:
I am experienced wiring, graduated in electronics :lol: Checked the controller wiring, still ok.
Checked the Vaillant manual but it only shows the controller wires going to terminal connector of the main circuit board in the boiler, but there is no schematic of the board itself :cry:
I power cycled the boiler yesterday and it has been ok since but suspect there may be a problem with the main board :cry:
getting closer to resolving I think.
I discovered the radiators only get hot when I turm on the hot water.
Boiler display shows 5 which is for DHW ( 4 is for CH).
I cheacked the manual and for CH and DHW it says to operate them and check position of the diverter actuator.
Fow heating the divertor moves down, then back to centre when off.
For water it stays centre. I feel the heating pipes and they get hot!!!
Am I right in thinking for hot water only the actuator of the divertor should be in top position not allowing flow to heating? Looks like that in the pic in the manual.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!