I've just replaced a light switch with a dimmer switch - the switch serves a ceiling light in which I've been using three 25w candle bulbs. The dimmer switch is wired EXACTLY the way that the instructions gave and also matches any pictures I've found on this site - ie. red to common and black to L1.
Both the light and switch work fine, but when the light is swtiched off the filaments in all three bulbs continue to glow. Have I done something wrong or is the switch faulty?
Hi, 2 possibilities, if switch has an OFF position ie either push on/off or a 'click' off then switch duff.
If no definite off pos. dimmer may be over rated for load, although rating for max may be ok there will be a minimum load as well.
for your 75W load a max of 250W would be normal rating which should go down to a min. of 60W, however if your dimmer is rated higher, say 400W
then minimum may be 100W so won't go completely off with 75W load.
Try putting 40W lamps in, you can dim them after all if too bright and you only pay for what you use,
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!