I have two 3 tier post and two spotlights that I would like to wire from the fuse panel. The dilemma I have is the post lights need to be switched ( have a light switch) and the two spotlights don't. Can I run these on the same 20 amp circuit? I already know how to install the switch. I just don't wanna overload or have any issues in the future. All suggestions will be appreciated.
There is a regulation - 433.4 Overload protection of conductors in parallel - which quotes "Where a single protective device (namely a fuse or MCB) protects two or more conductors in parallel there shall be no branch circuits or devices for isolation or switching in the parallel conductors". I think this concerns your particular requirements.
Also why a 20A MCB?
Use a 6A MCB to protect the switched tier lamps and can't you simply plug the spots into an existing socket outlet? A 3Amp cartrige fuse in the plug top would be suffice.
If this is in the garden as i suspect it is then use RCBO's (unless the circuits are alrady RCD protected). Just use appropriate external cable and you're laughing.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!