Hi Keith, I thought I had answered this ? yesterday but it seems not to have made it so here goes agn.
Assuming your nearest socket is on ring (IE 2 cables & not a spur already) then you can run a single 2.5 mm.twin/e to your new socket, you must run in 'safe zones' so this means vert. down to within 150 mm of floor, then along to door way then either around doorframe in mini truncking or chased in (which may loosen frame) , then along skirting to below new skt. position , up to skt.
or at doorway you could bury cable in chase but must be covered by 'earthed metal covering' difficult to do. there are proprietory 'skirting trunkings' available to cover cables.
Another way would be to go up from original skt to ceiling corner and run along in 150mm 'safe zone' covered by coving and down to new position, agn. purpose made cove trunking now sold in 'sheds
Hi, you probably did answer this, i didnt realise that the posts are moderated before being posted, so i seem to have posted twice!
thanks for the reply, after reading various regs etc, i have gone for chasing up to ceiling level and running along the 'safe route' along the top of the wall/ceiling area. 'tis a long way round, but seems to be the one that will satisfy the regs the best.
This misses the doorway completely (chased in above) and stops that headache, but saves chasing in to the floorway or around the door.
thanks for the heads up on the coving trunking, didnt realise it was available, makes life alot easier!
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!