I want to change a ceiling rose fitting in our utility room. The applicable fuse covers the lounge, kitchen, WC as well as the utility room lighting, if that’s relevant. Having turned off the power I unscrewed the existing ceiling rose but found the terminals different from the new ceiling rose.
The existing rose has three terminals. There are 3 cables coming through the ceiling, all black red and earth.
All the earths are connected together but by-pass the ceiling rose.
3 reds wires are all connected to 1st terminal on ceiling rose.
2 blacks are connected to 2nd terminal on ceiling rose.
1 black is connected to 3rd terminal on ceiling rose.
The connections on the new ceiling rose are different like this:-
Live Loop Neutral
00 000 000
How must I connect the cables on to the new ceiling rose?
I have not been able to find a new rose with connections the same as my existing rose.
The light in the Utility Room is bog standard with just the one pull on/off switch, obviously not a dimmer.
I would be grateful for any advice that would help me to safely change the rose.
Before doing ANYTHING mark the black on its own with red sleeving or tape, this is vital as it is the switched live coming back to the light and if you mix it up with the other blacks you WILL end up calling a leckie, now see projects page by all means
3 reds go to centre 3 in your rose.
2 blacks go to rhs 3 plus flex blue
1 red covered blk as above goes to lhs 2 with brwn of flex
project has coloured drawing to help
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!