ericmark wrote:Yes where extra low voltage transformers are used it is common, as there is no provision to connect multi cables in the step down devices, so the switch backing box is used as a junction box.
thanks for that ericmark -not related to micromark are you? but if thats the case then why ever scince i was an apprentice back in the good ole days of 78 we were always told to wire 3 plate system and never put neuts in switches[what changed from then to now ericmark me ole mate].
Hi, nothing changed still can 3 plate but some times places such as mobile homes with limited access to lofts are wire under floor and feed up to lights via switches.
Also in 70's we didn't have ruddy continental/Asian fittings with no room for more than one cable, nor down lights with same problem!
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!