I am looking for some advice. I have looked through the pages on this site and have been unable to answer my query.
I am installing a new ceiling light. When I removed the ceiling rose, my wiring is of the old style. There were 4flex cables, each containing a live(red) and black (neu) cable, with an earth wire. The light that I am fitting has a simple 3-channel junction block with live, neutral and earth inputs.
Initially, I made the mistake of grouping all 4 neutrals and all 4 live wires together, resulting in the lower lighting circuit tripping off when i turned the light off.
Following that minor oversight on my part, I have noticed that there is nowhere for the switching wire to connect to.
I may be doing something completely stupid that I've never done before but to save myself constantly blowing house fuses, is anybody able to offer any advice?
Many thanks in advance