Please help.... I have an indirect vented system and can only get hot water by using my immersion heater but don't want to leave this on all the time! The central heating works great and all radiators get hot quickly but there is no hot water. The cylinder was replaced a couple of years ago and the diverter valve is new. When i switch the programmer to HW there is a lot of noise from the pump, which is silent on CH, but cold water flows freely from the taps ie no gurgling or airlock type sounds.... any ideas or advice would be welcome - thanks in advance
Hi John. I've just had a similar problem Turned out to be an airlock in the heating coil inside the cylinder. If you can access the CH top up tank try fitting a hosepipe over the vent pipe. Attach the other end to a cold tap. Then get an assistant to gradually turn on the tap whilst you observe the CH top up tank. If air bubbles come through the feed at the bottom of the tank leave tap running slowly until the air stops. This may well cure it.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!