probably needs a replacement diaphragm in the pressure differential valve.
This located at the bottom left of the boiler - just behing the CH/HW selector switch, drop the front panel and when the hot tap is opened the pin should come out and operate the microswitch - if the pin doesn't come out change the diaphragm.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!