just wondering..a kitchen with 1 washer, 1 fridge, and 3 double socket outlets. presumin kettle, toaster, microwave plugged in...would all this exceed a 20amp radial ciruit? or do you think i shud just run 1 more leg to end of radial and do away with it and make it a ring circuit..abit of a ball ache tho as its all been studded plastered and skimmed now with new chipboard flooring. dnt ask why its been wired like that in the first place. i wud of just stuck with the ring circuit but was sparks in before that has wired it as such im just pickin up where he left off.
It's a bit maginal even allowing for diversity, but the only long operating item is washer assuming cold fill, all others are short term ops. so probably be ok. depends upon protection type, ie fuse, MCB type 2 or type 3 as trip/blow levels/times vary greatly, is kitchen in use? can you get clamp-on ammeter on cable to check average / peak loads?
You know the other option so is it worth checking or just bite the bullet & go for ring...Regards SPARX
think i am just going to bite the bullet and go ahead with the ring. it may cause abit of mess but it seems to be the better option in the long run..plus i have got a spare 32amp MCB lyin around gathering dust..saves buuyin a 20amp..
thanks for the advise dan
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!