When you recharge the system to around 1.25 Bar cold, does the pressure hold. If it does then monitor the operating pressure as the system starts to heat. It should rise by approx 0.5-0.75 Bar during operation. If the pressure rises to around 3.0 Bar then water will be discharged via the PR valve and will result in low pressure when the boiler switches off and cools.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!