I intend to install a cable to supply power to a CU in an integral garage. I am a retired electrician, I passed my iee (16th) and Part P a good few years ago so I need some advice regarding current iee regulations. The cable needs to be taken from an existing Henley block on the consumer board (the existing CU’s are fully utilised with no free MCB’s). The cable will be appprox. 5 metre to the garage CU running in the under floor void (under floor boards) across the house and through the house wall into the garage). Question :- Does this require a separate isolation switch at the consumer board but after the Henley block given that the cable run is approx. 5 metres and will this require additional protection at the house wall e.g. conduit etc.
Hi itsmalc Suggest your cable to the garage is armoured cable, you will need to fit an additional CU near to the Henley block or replace an existing CU to give you more ways. You probably need to involve an electrician. Regards S
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!