Old c. 1980's open vented c/h ssystem has had additional 6 rads added in loft conversion. F & E tank is on 5th floor of old mill, boiler & circulating pump are on 2nd floor. Has the additional rads taken the pump or boiler over their limit? Heat can be got to rads individually but not at same time. Have been told that the hot water pipe may have been connected to the c/h pipework? would heating or hot water work if this were the case as we still have hot water?
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!