Hi I want to replace an old aerial splitter box with a newer one. Labgear LDA2081LR Distribution Amplifier The old one looks to be powered by a cable connected to the lighting circuit. See photo The new labgear has a 3 pin plug on it. See photos of new splitter statistics and the old box connection Is it ok to either :- take the 3 pin plug off and wire in the new one exactly the same way as before? or replace the plate at the end of the lighting run with a 3 pin socket and then just plug in?
You have to understand why the previous person installed a "clock socket" first.
As you said it is supplied by the lighting circuit. Lighting circuits are rated at 5 or 6 Amps maximum. So if you were to change the clock socket to a normal 13A socket, anyone could be tempted to plug in something higher rated, this would blow the lighting fuse/mcb as it would be drawing too much current, so to prevent this the previous person has installed a clock socket.
Your best option would be to remove the plug from your new aerial amplifier and replace it with the plug from the clock socket. Also as its a clock socket, you just unplug it to change the cable to your new device, that way you can keep the lights on to see what you are doing.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!