I would like to replace the wires in the shed and I wanted to know if I am going about this correctly. Currently, there is a feed coming from a socket in the house, under ground in the garden and into the shed. It goes into a double socket, then out of that and into a light switch powering a tube light.
I would like to take the wire that's coming from the house into a fused switch, out of that into a 2 way junction box. One wire out of that will go to a double socket, the other will go to a double light switch running 2 led lights. I have attached my amateur drawing of what I would like to do.
What I am replacing was done about 20 years ago, if not before. From what I can gather, the wire goes back to a socket in the house which goes back to the consumer unit. On that breaker on the cu there is the sockets of one room, plus the shed. I do not know the spec of the cable that feeds any of this.
I intend on having an electrician inspect this but I am just wondering if I am OK to attempt this setup.
The fused connection unit is there to protect the cable for the lights (in this case) which is why it must be before the lights. The socket cable should be 2.5mm and the lighting cable should be either 1mm or 1.5mm.
I am only now getting round to attempting this project and I have hit a bit of confusion when connecting up the lights. The supply comes in to the double switch from a fused connection unit as suggested above. However, wiring the two lights to the switch doesn't seem to match any instructions I've come across. I've made a diagram of the best attempt I've made to wire it up, which is attached below. If anyone can make sense of this image, could they let me know if I have wired this correctly.
To try to help you understand, I will explain what is wrong with your drawing.
Light #2 will never work as it is only connected to the switch. Light #1 Will work when you turn on the supply, but when you turn off the switch there will be a big bang, and nothing will work again.
In order for a light to work it requires Live And Neutral. Light #2 the L & N are only connected to the switch, not the supply. Light #1 will work when you turn on the supply because it will have Live and Neutral, but when the switch is operated you will connect Live at the top of the switch to Neutral on the bottom right of the switch, creating a dead short, so the fuse will go Bang.
You should buy some wago connectors, and use these to connect all 3 neutrals to each other. (N in, N to light #1, N to light #2)
The Live coming in connects to the top terminal of either switch (It will be called C or L1) You should then take a link from this terminal (of which ever switch you chose) to the same top terminal on the other switch. The Live from each light goes into the bottom Left terminal of each switch. (Two switches, two bottom left terminals, so one wire in each terminal) Your earth connections are correct.
Again Mr White, your answer here clarifies everything, thank you very much. I'll now be able to connect it all up tomorrow. I won't turn the power on to the shed before I get someone to have a look over it but I will be able to get everything ready first. Thanks again! Richie
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!